- FEATURED PRODUCTS
- Solar Panels
- Solar Power Systems
- Battery Backup Solar Power Systems
- Puerto Rico Solar Products
- Charge Controllers
- Deep Cycle Batteries
- MORE PRODUCTS
- Cables & Wiring
- Enclosures, Electrical & Safety
- Heat Pump Water Heaters
- Inverter Power Panels
- Meters, Communications & Site Analysis
- Portable Power Systems
- Refrigerators & Freezers
- Solar Panel Mounts
- Solar Water Pumps
- Voltage Converters
- Wind Turbines
- * Clearance Sale *
Square D DU322RB 60A 240VAC Unfused Disconnect, 3 pole
|Item code||Brand name||Model number||Amps|
Please see OFFER SAFETY ALERT on this Product - WARNING of potential unsafe condition of certain Square D products purchased from Jan 2014 - Jan 2018. **The safety switch can potentially remain energized when the handle is in the "OFF" position, which poses potential risk of electric shock to consumers. Please click on link for suggested course of action from Manufacturer.
Don't forget to order the Ground Kit for this item!
Nema 3R Disconnects
According to the National Electric Code, section 690.15, PV arrays must have a disconnecting means to isolate the inverter from the PV power source. Utility intertie inverters that utilize PV arrays with voltages above 250 VDC require a disconnect rated for 600 VDC to perform this function. The Square-D 600 VDC 30 amp 3-pole safety switches are UL listed to handle 13A at 600VDC per pole. They can be used for disconnecting up to three PV arrays for three grid-tie inverters. It has wiring lugs that are rated to accept two #14 to #10 wires in each lug. This allows the disconnect switch to also act as a string combiner in systems that utilize two strings of PV modules per inverter. All other Square D 600 VDC disconnects are rated for disconecting one string at full rated power.
Many utilities require an AC disconnect between an intertie inverter and the AC load center, close to the AC service entrance, with a visible and lockable handle. A 30 amp 240 volt disconnect is good for up to 5kW at 240 VAC (one or two 2500W intertie inverters) and the 60 amp disconnect is good for up to 12.5kW (three to five 2500W intertie inverters). For connection of multiple inverters to one of these disconnects, use an AC load center, with a circuit breaker for each inverter installed, as an AC combiner box between the inverters and the disconnect switch.The breakers can be back-fed with the inverter outputs and the load center main lugs will handle the combined outputs to be connected to the AC disconnect.
Use Class-R fuses of the proper amperage for fused disconnects. Disconnects are raintight (NEMA 3R) for outdoor use.
|Model||Maximum Voltage||System Voltage||Poles||Ampere Rating||Enclosure||Dimensions||Weight||Fusible|
|H361RB||600 VAC/ VDC||600 VDC||3||30 Amp||Nema 3R||14.88" x 6.63" x 4.88"||9.8 lbs||Yes|
|DU221RB||240 VAC||240 VAC||2||30 Amp||Nema 3R||9.63" x 7.25" x 3.75"||4.4 lbs.||No|
|D221NRB||240 VAC||240 VAC||2||30 Amp||Nema 3R||9.63" x 7.25" x 3.75"||4.5 lbs.||Yes|
|DU222RB||240 VAC||240 VAC||2||60 Amp||Nema 3R||9.63" x 7.25" x 3.75"||4.5 lbs.||No|
|DU322RB||240 VAC||240 VAC||3||60 Amp||Nema 3R||9.63" x 7.25" x 3.75"||4.5 lbs.||No|
|D222NRB||240 VAC||240 VAC||2||60 Amp||Nema 3R||9.63" x 7.25" x 3.75"||9.65 lbs.||Yes|
|D223NRB||240 VAC||240 VAC||2||100 Amp||Nema 3R||17.5" x 8.5" x 6.5"||15.46 lbs.||Yes|
There are no reviews for this product.