solar power for aviary

1 Posts
Jan 14, 2006 01:25 pm
solar power for aviary

Am planning to build an aviary which will require occasional heating by season (I live in So. California) plus a small fan plus lights (15 Watts). Is an independent solar power unit suitable under these circumstances? Or should I just go gas heater and convential lighting source? Thanks.

Jan 15, 2006 02:33 pm
Re: solar power for aviary

Heating is more efficient with solar when direct solar heat gain is used, whether water or air is used as opposed to using PV to to make electricity to make hot water or air. Although by heating water one can have storage for non-sunny days.
PV can simplify the system and give storage.
The cost can get high though, low voltage dc water heating elements are not cheap when compared to there 240 vac counterpart and there realitivly higher wattage capabilities. A circulating pump might be needed as well as an air handler (small radiator).
I have never expierienced Southern California Winters so I have to imagine that the days are cool while the nights can get cold so storage might be nescessary. I've always heard the expression "Sunny California," so even when the days are cool I guess the Sun shines most of the time?
Would it be possible to construct part of the aviary as somewhat of a "greenhouse?" Using a thermal mass such as black tanks of water and or large stones?
The fan and light lend themselves well to PV modules. Simply add the wattages of the two and multiply that by the number of hours expected to run in a twenty four hour period, multiply that by five and then divide by a nominal voltage in order to get the amount of battery storage for about four days without sunshine.
Example;
fan  15  watts
lights  100 watts
totals  115 watts
X   10 hours
=  1150 watt hours
X     5  (20%)
=  5750 watt hours
/    48 vdc nominal
=   120 amp hours of battery storage.
Now to replace whats used in a twenty four hour period within one good sunny day, first know the average number of hours of full rated charge from a PV module in your region, angled perpendicular to the Winter time Sun at noontime on the shortest day (Dec. 21).
I'am going to geuss at 5 hours. So;
1150 / 5 = 230 watts of PV array at 48 vdc nominal.
Whichever you chose you may not want to rely on one thing only. Always have a backup.
Hope this helps.

462 Posts
Jun 8, 2006 01:59 pm
Re: solar power for aviary

if you are going to have a concrete floor, using radiant heat will work well with solar hot water along with some passive gain onto the slab. Condider insulation in walls and for windows. With SHW, when your not heating, and even when you are heating, you can use it for domestic hot water. As far as lighting goes, natural daylighting, especially for animal is the best way to go. If you want to go PV, go 12 v with 12 v lighting, either automotive, LED, flourescent or UV. You can get 12 v fans at radio shack....

Disclaimer and Disclosure

The Alternative Energy Store, Inc reserves the right, within its sole discretion, to refuse or delete any posting or portion thereof, or terminate or block the access to this forum.

The opinions and statements posted on this forum are the opinions and statements of the person posting same, and do not constitute the opinion or act of the Alternative Energy Store, Inc (AltE). The Alternative Energy Store, Inc does not endorse or subscribe to any particular posting. No posting shall be construed as the act or opinion of the Alternative Energy Store, Inc.

Share

Click on an icon to share! If you don't see the method you want, hover over the orange "+".

Feedback

What can we do to help you?

Please enter a summary
Sorry, the copyright must be in the template.
Please notify this forum's administrator that this site is using an ILLEGAL copy of SMF!