# Battery bank for swimming pool

2 Posts
Nov 13, 2014 09:41 pm
Battery bank for swimming pool

Is this calculation right?

i have a pool with a 1hp pump - or 743W, say 750W

Following the method on this site:

- pump only: 750W, working 10H full time: 7500 Wh/day
- 2 days back up: 15000 W
- Depth of Discharge: 40%:       15,000 Wh/40% = 37500 Wh
- Temperature factor: 1      37500Wh
- System Voltage: 24V deep cycle batteries >>    37500AVh/24V = 1563 Ah  (top up to 16750 Ah for calc)

say w/o inverter, just an oscillator, 24V and 250Ah batteries:

250 Ah: 1750Ah/ 250Ah = 5 such batteries in parallel
24 V: 220V / 24 = 10 strings in serials

That is 50 batteries for a 750W pump?  My calculation must be wrong somewhere.

And how to calculate the bank if an inverter is to be used?

Thanks
Marc C

47 Posts
Nov 18, 2014 01:53 pm
Re: Battery bank for swimming pool

You almost had it right, just made a slight mistake at the end.  First, let's include the inverter, you divide the watt hours by the inverter efficiency.  Let's guess 94%.  37500WH / .94 = 39,893WH / 24v Battery bank = 1662ah.

Your mistake came with calculating the voltage.  You are  now figuring a 24V 1662ah battery bank, so if you figure using 12V 250ah batteries, that's 1662ah / 250ah batteries = 6.6 parallel strings, round up to 7.  24V battery bank / 12V batteries = 2 in series.  7 strings of 2 = 14 batteries.

However, I recommend you don't do 7 strings in parallel, that can lead to uneven charge/discharge cycles, shortening the life of the bank, so if you did a 48V system, 39,893Wh / 48V = 831ah 48V battery bank.  831ah / 250ah batteries = 3.3 strings, round up to 4.    48V battery bank / 12V batteries = 4 in series.  4 x 4 = 16 batteries.

Hope that helped.

Amy
altE store
Solar Queen

2 Posts
Nov 18, 2014 07:42 pm
Re: Battery bank for swimming pool

Thank you.

The reason why my calculation was w/o inverter is that in Spain they avoid using those and simply add an oscillator.
So I did the calculations to check where the benefit could be in doing so. Other than the % loss because of the inverter I do not see an immediate advantage indeed.

A good day to you,

47 Posts
Nov 19, 2014 10:04 am
Re: Battery bank for swimming pool

Ah, that explains the 220V in the battery calculation. Then yes, you were right, 220V / 24V batteries = 9.1, round up to 10 batteries in series.

But if you are using 220V as the battery bank voltage, you would do
37,500 wh / 220V = 170ah / 250ah battery = .68, round up to 1 string of 10 24V 250ah batteries.

Disclaimer and Disclosure

The Alternative Energy Store, Inc reserves the right, within its sole discretion, to refuse or delete any posting or portion thereof, or terminate or block the access to this forum.

The opinions and statements posted on this forum are the opinions and statements of the person posting same, and do not constitute the opinion or act of the Alternative Energy Store, Inc (AltE). The Alternative Energy Store, Inc does not endorse or subscribe to any particular posting. No posting shall be construed as the act or opinion of the Alternative Energy Store, Inc.

## Share

Click on an icon to share! If you don't see the method you want, hover over the orange "+".