Call for AvailabilityEstimate Shipping
|Item code||Model number|
|KITONGRID-F||Grid-Tied Package F2.94kW|
Residential Packaged System
Solar Panel Package - Utility Grid Tied for the Energy-Efficient Residential Home
This a grid-tied system for a residential energy-efficient home. The output of this system varies depending upon where you live and what time of the year it is. Use the map at the bottom of the page to get an idea of how many Watt*Hours you can expect from your system on average during a typical year. Expect more ouput in the summer (highest output period) and less in the winter (lowest output period). Please consult the Photovoltaic Power Systems And the 2005 National Electrical Code: Suggested Practices Photovoltaic Power Systems publication for information regarding electrical wiring requirements.
1. Photovoltaic Modules (aka solar panels, solar electric panels)
The PV modules are the individual building blocks for providing power from the sun. They are typically made from silicon cells, glass, tedlar, and aluminum. PV modules can vary in type, size, shape, and color. The common nominal voltages for modules are 12V and 24V, but newer modules that are intended for grid tie systems, often now have much higher voltages to accommodate the voltage windows of grid tie inverters. Costs for PV modules are currently averaging around $1.00 - $2.00 USD per rated watt.
2. Racking/Mounting System for PV modules
The mounting system for the PV modules includes the hardware to permanently affix the array to either a roof, a pole, or the ground. These systems are typically made of aluminum and are customized to the mounting surface and the model of module used. It is important to consider distance from roof for flush-type roof mount installations. Restricting airflow under the modules results in higher module operating temperatures that reduce power output. With pole mounts wind loading must be considered and proper civil works must be done with the foundation for the pole as well as the possible addition of supplementary wind supports for the array frame. The cost of a mounting system can vary drastically based upon the number of modules and type of mount. The average cost is between $250 and $1000 USD.
3. Combiner Box
A combiner box is an electrical box where series strings of PV modules are then spliced in parallel. This is also the place where the PV series string fuses or circuit breakers are located. This allows the installer to bring the separate strings together and combine them into one positive and one negative conductor, change wire types and leave the area of the modules in conduit. They are usually outside and weather rated, so they can be right next to the array. Combiner boxes usually cost between $80 and $140 USD.
4. DC and AC Disconnects
The DC and AC disconnects are manual switch units that are capable of cutting off power to and from the inverter. Some inverters have disconnects integrated into the unit with switches, others can have them integrated into a power panel assembly, and some inverters leave you on your own to provide suitable disconnecting means. The disconnects are used by service personnel or authorized persons (fire/police/electric workers) to disable power from a renewable energy system (in this case PV) so that there are no live electrical parts associated with the inverter, and that no current is going to the grid that could harm utility employees in the event that they are working in your area. Homeowners or authorized personnel can use the disconnects to de-energize a system for maintenance or service. Disconnects can range in cost from $100 to $300 USD.
5. Grid Tie Inverter
The grid tie inverter is the device that takes the energy that the photovoltaic system produces in DC current form and turns it to AC current that is then sent (sold) to the electric grid. These inverters typically have a voltage input range from 100 to 500 volts DC and they convert it into 120 volts AC, 240 volts AC, or 208 volts AC. These inverters are especially sophisticated devices that must conform to special regulations in order to tie into the utility. When the power goes out in your area, it is important to know that the grid tie inverter will not allow power to be sold back to the grid. This is done to prevent electric utility workers from being injured or killed by working on power lines they thought were de-energized. When the power goes out, your power will go out as well. A grid tie inverter will not resume normal operations until the utility grid has established standard conditions for 5 straight minutes within strict parameters. Prices for inverters can range from $1400 to $4000 USD.
Frequently Asked Questions
1. How do I find my total energy usage or the "loads" of my appliances?
Step 1: Calculate loads of household appliances (in watts):
a. You can find a listing of common appliance wattage ratings here.
b. You can also use a Kill-A-Watt meter, which gives readings of how much
instantaneous power and energy an appliance is using.
Step 2: Calculate total energy usage (in watt hours per day)
a. Use the load information you just assembled with our load calculator to find out how many watt-hours you use per day.
2. The label on my appliance does not list Watts, it only lists Amps. How do I find the wattage?
Converting from Amps to Watts is a simple calculation: Watts = Amps x Volts
Our household voltage is 120 Volts AC. If we have a television that lists 1.5 Amps, we calculate the wattage as follows:
1.5 Amps x 120 Volts = 180 Watts
3. My refrigerator lists kilowatt hours per year. What wattage do I enter in my load calculator?
Convert kilowatt hours per year to watt hours per day by the following calculation:
Kwh x 1000 = watt hours per year
Watt hours per year / 365 days per year = watt hours per day
4. How do I know what size PhotoVoltaic system I need for my energy usage?
To get a better idea of system size, take the data from your load calculator and use it in one of our system calculators, either for on-grid or off-grid applications.
5. How do I figure out the likely energy production of a given system which lists rated Watts of PV?
Step 1: Look at the solar insolation map below to find you average sun hours per day.
Step 2: Multiply the rated Watts of your system by the amount of sun hours per day to get the average Watt-hour production number.
Step 3: Decrease the calculated amount by about 20% to take into account system inefficiencies. This will provide a more realistic view of the system production. (**The 20% reduction is to be conservative. That way your production should not fall short of your usage.)
Here is an example:
Calculate the predicted energy production of a 1 kW PV system in Pittsburgh, PA.
- The solar insolation for the Pittsburgh area appears to be about 4 hours.
- 4 sun hours x 1000w = 4000 watt-hours
- Decrease that number by 20% (or multiply by 0.8): 4000 x 0.8 = 3200 watt-hours per day = 3.2 kilowatt-hours per day.
Note: It is important to know that the sun hours for your area change based on time of year. Average daily sun hours provide an estimate to calculate the approximate size of a system. If you are completely off the grid (not connected to utility power), and rely on PV to produce all of your electricity, you will want to have more accurate calculations. To be more accurate, use data close to your area that is broken down by month, compares the angle of PV modules, and includes information on whether or not you have an active tracker for your array. This data can be found in reference materials like the Photovoltaics Design and Installation Manual.
Find the average annual insolation for your area below.
This item is a package made up of the following components. Please call to speak to a sales representative to learn about other options which may be available.
There are no reviews for this product.
Do you own this product? Write a review